For All The Supplies And Products You Need
Our Experienced Staff Can Help Make Your New Building Project a Reality.
- Receipts required for all returns
- No returns after 60 days
- No returns for special orders
- Returns picked up with our trucks are subject to a restocking charge
Septic Tank Installation Guidelines
The site must be accessible to large, heavy crane equipment. A firm, level area must be provided to permit for safe unloading by our operator. It must be free of overhead wires (the Electrical Safety Authority recommends a minimum 10’ clearance from any lines), tree branches or other obstructions that could affect crane operation.
Septic tanks are typically of a weight that requires them to be unloaded from the rear of the truck. We may need to be within 3 to 10 feet (1 to 3 metres) of the excavation to unload depending on the size of the tank.
Our drivers are instructed not to unload in any condition that might compromise their safety or cause damage to our equipment.
Please ensure utility locates are completed prior to excavation. A minimum of 12” (300mm) clearance is required on all sides to allow us to remove our lifting equipment following placement. More space needs to be allowed if work needs to be done to the exterior of the tank after placement.
The excavation must be level and free of large rocks and stones. We recommend a base of gravel or crushed stone be used minimum 6” (150mm) deep for all installations but require it for all installations of tanks 2000 gallon (9000L) or larger. In unstable soil conditions or in areas where there is a high water table it is the responsibility of the contractor to ensure that suitable bedding material is used.
Large rocks or saturated clay should not be used as backfill material or to cover the tanks. Backfill should not be dropped from a height greater than 3’ (1m). The maximum depth that our tanks may be buried is also 1m. Equipment should not be closer to the tank than the line of excavation and at no time should drive onto the tank. Excavating equipment should not be used to push on the tank to level it or move it. Care should also be taken to backfill tanks in high water table areas before they have the opportunity to float.
Our tanks are engineered to rely on the surrounding earth for support. At no time should the liquid level on the inside of the tank exceed the level of backfill by more than 2 feet (600mm). If testing is required make sure ample time is given to allow the mastic to settle (typically 24 hours) and the tank has been backfilled.
- A Maximum of 6 Customers in the Showroom at one time
- Please use the Hand Sanitizer Provided
- If you are sick or have any symptoms such as a cough or fever you are not permitted in the store
- We have mandated that our employees practice safe social/physical distancing of 2 metres (6’)
- If you are waiting for service please wait on the designated spots
- We currently have no public washroom available
- While we still accept cash we encourage you to use Debit or Credit
Monday-Friday: 7 a.m. – 5 p.m.
Saturday: 8 a.m. – 1 p.m.
Monday-Friday: 7 a.m. – 4 p.m.
Quality Landscape Products
We deal with a wide variety of top brands.
Quality Masonry Products
Our experienced staff can help make your new building project a reality.
Septic Tank Products
We have been manufacturing high quality septic tanks since 1966.